Conventional wastewater treatment is not sufficient for the removal of hygienically relevant bacteria and achieves only limited reductions. This study focuses on the reduction efficiencies of two semi-industrial ultrafiltration units operating at a large scale municipal wastewater treatment plant. In total, 7 clinically relevant antibiotic resistance genes, together with 3 taxonomic gene markers targeting specific facultative pathogenic bacteria were analysed via qPCR analyses before and after advanced treatment. In parallel with membrane technologies, an ozone treatment (1 g ozone/g DOC) was performed for comparison of the different reduction efficiencies. Both ultrafiltration units showed increased reduction efficiencies for facultative pathogenic bacteria and antibiotic resistance genes of up to 6 log units, resulting mostly in a strong reduction of the bacterial targets. In comparison, the ozone treatment showed some reduction efficiency, but was less effective compared with ultrafiltration due to low ozone dosages frequently used for micro-pollutant removal at municipal wastewater treatment plants. Additionally, metagenome analyses demonstrated the accumulation of facultative pathogenic bacteria, antibiotic resistance genes, virulence factor genes, and metabolic gene targets in the back flush retentate of the membranes, which opens further questions about retentate fluid material handling at urban wastewater treatment plants.
Antibiotic Resistance Genes and Facultative Pathogenic Bacteria in Wastewaters
Antibiotic resistance genes (ARGs) and facultative pathogenic bacteria from different origins (hospitals, nursing homes, housing areas, slaughter houses etc.) that pass through treatment plants or agricultural runoffs can lead to a contamination of environmental water resources. In certain circumstances this could cause an impairment of human health in case of direct contact and colonisation1,2,3,4. As released bacteria are able to persist in the aquatic environment and may proliferate back to critical concentrations, an ecologically worthwhile solution is recommended5.
Besides facultative pathogenic bacteria, which can be the causative agents of human and veterinary infections, antibiotic resistance genes are also a point of interest. Their distribution via horizontal gene transfer can occur regardless of their initial origin species, and once released to the environment they are able to transfer to autochthonous bacteria as well as other facultative pathogenic bacteria6. This critical ability might lead to an overall increase in antibiotic resistance in their respective habitats. This process is supported by the presence of antibiotics, which even in sub-inhibitory concentrations by medical means, favours horizontal gene transfer e.g. in wastewater treatment plants7,8,9,10,11.
Conventional wastewater treatment is not sufficient to entirely remove biological contaminants (bacteria, viruses, and protozoa)2,12. Even tertiary treatment with activated charcoal (GAC, PAC) showed insufficient impact on biological contamination in discharges13. Up to date ARGs are mentioned in neither drinking water nor wastewater specific regulations or surveillance strategies, despite the World Health Organisation (WHO), as well as the plenum of the United Nations (UN), demanding a disruption of their means of distribution14.
Ozonation is already discussed as a possible disinfection process, having already proven its capability to degrade and/or transform micro-pollutants and, in some studies, reduce facultative pathogenic bacteria and ARGs15,16,17. Nevertheless, it is known that ozonation might introduce selection for robust bacteria, including facultative pathogenic bacteria, that have subsequent possible regrowth potential12. Another drawback of ozonation is the unpredictable formation of unwanted by-products5,17,18.
Ultrafiltration is an alternative process to separate facultative pathogenic bacteria and ARGs from the wastewater effluents. Whereas ozonation targets DNA and other cellular structures, aiming towards inactivation or killing of bacteria19,20, ultrafiltration retains bacteria, including antibiotic resistant microbes, by the physical properties of their membrane. This occurs either through direct size exclusion or adsorption processes. Beside bacteria, free floating nucleic acids attached to particles can also be reduced21.
This study aimed to develop a deeper understanding of the ultrafiltration reduction efficiencies of facultative pathogenic bacteria and ARGs in comparison to ozonation at an urban wastewater treatment plant (WWTP). Drawbacks of ozone and especially membrane technologies are mentioned and also analysed with the help of modern molecular biology analyses for subsequent risk analysis. More specifically, the often neglected retentate as side product of the ultrafiltration and its inherent health risk is accounted for, as well as the influence of the ultrafiltration fluxes on the elimination effect.
Material and Methods
The investigated WWTP is located in the south-west of Germany and treats the clinical, industrial, and municipal wastewater of 440,000 population equivalents. Volumes of 80,000 to 100,000 m3 of wastewater are treated per day before the conditioned waters are released into the river Danube. The treatment consists of conventional mechanical and biological stages, along with a precipitation clearance. The mechanical treatments included a sand and grease trap, followed by a fine screen, and finally the primary sedimentation basin. The biological treatment consisted of three treatment steps, starting with biological phosphorous elimination, followed by a two-step nitrification/denitrification stage, and then further clarification through a secondary clarifier.
The two ultrafiltration (UF) units were both designed in semi-industrial sizes and contained hollow fibre modules with an organic membrane material. The UF units were provided by membrane producing companies (MICRODYN-NADIR GmbH, Wiesbaden, Germany and INGE GmbH, Greifenberg, Germany). Both companies are directly cooperating with German and international water industries. Organic membranes were chosen in respect of later up-scaling and economic reasons, as the operation of the alternative ceramic membranes are not economical in large scale systems. Here, the organic membranes allow flux rates up to 90 L/m²h at a transmembrane pressure of up to 1000 mbar22.
Ultrafiltration 1 (UF1) had a membrane surface of 80 m² and was operated in inside/out mode and utilised a membrane with a nominal pore size of 20 nm. The filtration was performed at a flux of 70 L/m²h. Ultrafiltration 2 (UF2) was operated in an outside/in mode with a nominal pore size of 25 nm and with the addition of a precipitating agent (polyaluminumchloride) performed at a Flux of 35 L/m²h. Flushing of the retentate of both membranes was performed every 45 minutes with water and air. Additional backwashing to remove scaling of both membranes was performed with a mixture of 30% NaOH and 5% NaClO, followed by a second washing step with 30% HCl were executed less frequently and on demand to ensure stable conditions. During the project, both ultrafiltration units were operated with the outflow of the upstream biological treatment.
The ozone facility (OCS-GSO30, WEDECO, Herford, Germany) operated with an ozone concentration of 1 g ozone/g dissolved organic carbon (DOC) and a flow rate of 7 m³/h, which resulted in an ozone contact time of 5 minutes. Ozone concentration of 1 g/g DOC was chosen in respect to micro-pollutant removal. As considerable higher ozone concentrations at 1.5 g ozone/g DOC were observed to have an eco-toxicological effect and would therefore not be appropriate regarding the complete wastewater treatment process without further treatment steps23. The facility utilized diffusers for ozone intake and a catalytic ozone destructor to withhold the remaining gaseous ozone. DOC measurements were performed just before each sampling.
During the sampling period from February till November the treatment plant operated without failure and the relevant parameters of the wastewater utilized for advanced treatment techniques were recorded hourly. The mean pH value of the wastewater was 8.1 ± 0.7 and the average water temperature was 16.0 °C ± 3.2 °C. Further monitored water specific parameters were DOC with 4.3 g ± 1.2 g, conductivity with 828.1 µS/cm ± 193.1 µS/cm and the SAC (spectral adsorption coefficient) with 9.4 ± 1.7. These circumstances have to be considered as especially ozone treatment is dependent on the DOC, temperature, and organic compounds. Most favourable conditions for an ozone treatment would be, low DOC and SAC values, temperatures above 25 °C and a pH-value of 7.0)24. As the temperature of the system is highly dependent on the season, the pH-value is nearly optimal for an ozonation. The elimination efficiency of ultrafiltration itself is almost independent of the composition of the treated water. Solely, frequent occurring scaling and fouling causes a decrease of membrane overall lifespan and increases the energy required to maintain a specific flux rate and have to be approached accordingly25.
Both ultrafiltration and the ozone treatment were studied simultaneously for better comparison of the technologies and reduction efficiency results (Fig. 1).
Sampling, sample preparation, and DNA extraction
For evaluation of the ultrafiltration and ozone reduction efficiency, 4 sampling campaigns were performed during 9 months (February till November, 2017). Additionally, two samplings with different flux rates (12.5, 50, 90 L/m²h) were performed for ultrafiltration. Inflow and outflow of the membrane facilities, as well as back flushed water, containing the retentates of both ultrafiltration units were analysed in parallel. Volumes of 10 L of each UF filtrate, 750 mL of ozoned water, 300 mL of inflow, and 400 mL of flush-water were vacuum-filtrated through a 0.2 µm polycarbonate membrane (Whatman Nuclepore Track-Etched Membranes, Sigma-Aldrich, Munich, Germany). After the filtration process, the membranes were treated with 0.25 mM propidium monoazide (BLU-V viability PMA-kit, Quiagen GmbH, Hilden, Germany) to complex free DNA as well as DNA from dead or injured bacteria26. DNA extraction from the filtered biomass at the membrane was performed using the Fast DNATM Spin Kit for Soil and FASTPREP® Instrument (MP Biomedicals, Santa Ana, CA) according to previous studies and stored until further analysis at −20 °C2.
Taxonomic marker genes and antibiotic resistance genes
All qPCR systems targeting ARGs and marker genes specific for facultative pathogenic bacteria were analysed for specificity and sensitivity using reference bacteria according to Hembach et al.2. Full primer sequences are listed in the Supplementary Information (SI Table 1). Escherichia coli (yccT gene) (4), Acinetobacter baumannii (secE gene27), intestinal enterococci (23S rRNA gene) (4), and the 16S rRNA gene for eubacterial determination were quantified. The antibiotic resistance genes sul1 (sulfamethoxazole resistance)28, blaTEM (β-lactam resistance)28, and tetM (tetracycline resistance)29 were studied as they represent the most frequently detected ARGs in urban wastewaters2. The antibiotic resistance genes CTX-M30, CTX-M-3228, blaOXA-48 (carbapeneme resistances)31, and blaVIM (Imipenem resistance)32 were also analysed. Furthermore, the resistance genes CMY-2 (against Cephalosporines)33, vanA (Vancomycine resistance)34, mcr-1 (Colistin resistance)2, and blaNDM (New Deli-beta-lactamase)31 were monitored as they represent resistances against last line of defence antibiotics.
For qPCR analysis a Bio-Rad Cycler CFX96 (CFX96 Touch™ Deep Well Real-Time PCR Detection System, Bio-Rad, Munich, Germany) was used. All samples were measured in technical triplicates. The specific taxonomic and resistance directed genes in the entire bacterial community were quantified utilizing a SYBR Green qPCR approach according to Hembach et al. and Jäger et al.2,3. Reactions were run in volumes of 20 µL, containing 10 µL Maxima SYBR Green/ROX qPCR Master Mix (2×) (Thermo Scientific, Nidderau, Germany), 8.2 µL of nuclease-free water (Ambion, Life technologies, Karlsbad, Germany), 0.4 µL of the respective primers (stock concentration 10 µM), and 1 µL of template DNA. The qPCR protocol comprised 10 minutes at 95 °C for activation of the DNA polymerase followed by 40 cycles of 15 s at 95 °C, and 1 min at 60 °C for primer annealing and elongation. Melting curves were recorded by raising the temperature from 60 °C to 95 °C (1 °C every 10 seconds) to determine the specificity of the amplification. This allows the evaluation of the amplicons based on their lengths and base pair ratios. Hence, higher AT content results in higher melting points at constant amplicon lengths. Data analysis was performed by using the Bio-Rad CFX Manager software (version 3.1 © 2012 Bio-Rad Laboratories).
An absolute quantification normalized to 100 mL water sample was performed to demonstrate the reduction effects of the applied treatment processes for quantitative analysis. Cell equivalent calculations based on the qPCR based Ct-values in the linear part of calibration curves2. The respective calibration equations of each target are listed in the SI Table 1. Calibration curves were obtained with reference strains carrying the corresponding specific ARGs or taxonomical marker genes.
These reference strains with known genome sizes, respective known plasmid sizes, were used to calculate cell equivalents utilizing the amount of DNA used for creating the target specific calibration curve. Equation 1 was used to create a correlation of the amount of DNA in the calibration solutions and the corresponding cell equivalents. It utilized an average molecular weight for one base pair of about 650 g/mol, Avogadro’s number with 6.022 × 1023 molecules/mol, and a converting factor of 109 ng/g.
Equation 1. Calculation of cell equivalents in a PCR-reaction based on the average molecular weight of one base pair, Avogadro’s number, the amount of DNA used for the reaction and a converting factor.
Limit of detection (LOD) of each detection system, ranging from 4 gene copies (E. coli yccT gene) to 126 gene copies (intl1 gene), are listed in the Supplemental Information (SI Table 2).
Extracted genomic DNA from the retentate of both ultrafiltrations was sequenced by Eurofins GATC Biotech GmbH, Munich, Germany and mapped against the MvirDB microbial virulence database and the integrated reference catalogue (IGC)35,36,37. Taxonomic profiling was done using Kraken and Mikrokraken reference database38.
The sequencing generated 22,545,798 reads for the retentate of UF1 and 23,480,814 reads for UF2 of which 3,387 (0.02%) and 3,428 (0.01%) reads were successfully mapped to a reference in the MvirDB database for resistance screening. 173,478 reads (0.77%) of UF1 and 153,226 reads (0.65%) of UF2 were successfully mapped against the integrated reference IGC catalogue for functional profiling. Taxonomic profiling yielded 739,418 (3.28%) classified reads for UF1 and 596,486 (2.52%) for UF2.
The raw sequencing data can be obtained as .fastq file at the NCBI database with the BioProject Accession number: PRJNA524456.
All cultivation analyses were performed immediately after sampling to minimize preselection bias during transport and storage. Different selective agar systems were used for the detection of E. coli (Chromocult-Coliform-Agar, Merck, Darmstadt), Acinetobacter spp. (Acinetobacter-CHROMagar, MAST Diagnostica GmbH, Reinfeld, Germany), intestinal enterococci (Slanetz-Barley Oxoid, VWR, Darmstadt and Bile esculin Agar, VWR, Darmstadt), and extended spectrum beta lactamase (ESBL) producing Gram-negative bacteria (CHROMagarTM MAST Diagnostica GmbH, Reinfeld). Three different sample volumes (750 mL, 1000 mL, and 1250 mL) were filtered through a 0.45 µm nitrocellulose membrane (GE Healthcare Life sciences, Solingen, Germany). The membrane was then transferred onto an ager plate and incubated under conditions recommended by the manufacturer. After an appropriate incubation time, Colony Forming Units (CFU) were determined for each plate and calculated as CFU per 100 mL. The mean of all three sample volumes were calculated for final evaluation.
DNA extraction was performed in technical triplicates and extracts were pooled afterwards for further measurements. qPCR was also performed in technical triplicates and their mean Ct-values were used for cell equivalent calculation of each target and sample. For statistical evaluation, the cell equivalent median from all four sampling campaigns was utilized for p-value calculation to verify the significance displayed in the figures. Due to the sampling periods (n = 4), significance was tested with a one tailed non-parametric Mann- Whitney- U test29.
Gene abundances of facultative pathogenic bacteria as well as ARGs are displayed as boxplot. Herein the edges between two different bars represent the median. The bars themselves represent the upper (p = 0.75) and the lower (p = 0.25) quantiles. Error bars illustrate the maximal and minimal abundances of the sampling point over the complete sampling campaign.
Results and Discussion
Comparative analyses of treated wastewater
Conventional treatment at the WWTP consisted of the mechanical removal of solids and biological treatment with sedimentation of sludge biomass. Hence, the treated wastewater, after biological treatment, was used as a reference value to compare the reduction efficiencies of the advanced treatment processes for facultative pathogenic bacteria and ARGs.
The eubacterial 16S rRNA gene marker was present at a concentration of 6.28 × 108 cell equivalents/100 mL after conventional treatment without any implementation of advanced treatment technologies (Fig. 2). Based on this, around 5.65 × 1017 cell equivalents of Eubacteria will reach the receiving river each day (based on 90,000 m³ per day). Specific gene markers targeting E. coli, A. baumannii, and enterococci were found in high abundances after conventional treatment as illustrated in Fig. 2. Here, these facultative pathogenic bacteria were present in the range of 1.63 × 103 to 2.01 × 104 cell equivalents/100 mL. The total abundances of the three facultative pathogenic bacteria (E. coli, A. baumannii, enterococci) reached together a calculated number of 2.66 × 1013 cell equivalents per day that are released to the riverside, when 90,000 m3 of conditioned wastewater per day was released from the WWTP into the receiving river.
Regarding the median of each specific target gene, ARGs in the effluent of the conventional wastewater treatment can be grouped in three different subgroups according to their remaining concentrations. Antibiotic resistance genes and the integron intl1 gene being quantified in high amounts of cell equivalents/ 100 mL were grouped as frequently detected genes. Herein, the genes blaTEM (β- lactam resistance against ampicillin) with 4.72 × 105 cell equivalents/100 mL, tetM (tetracycline resistance) with 6.31 × 104 cell equivalents/100 mL, sul1 (sulfamethoxazole resistance) with 1.25 × 107 cell equivalents/100 mL, ermB (erythromycin resistance) with 9.66 × 104 cell equivalents/100 mL and intl1 (class 1 integron specific marker) were categorized as frequently occurring ARGs (Table 1, Fig. 3). Less frequently occurring ARGs made up the subgroup of intermediately detected genes. This group consists of the genes CTX-M-32 (1.52 × 104 cell equivalents/100 mL), CTX-M (1.61 × 103 cell equivalents/100 mL), blaOXA-48 (1.67 × 103 cell equivalents/100 mL), CMY-2 (4.98 × 103 cell equivalents/100 mL), and blaVIM (4.92 × 103 cell equivalents/100 mL). The third subgroup consists of antibiotic resistance genes which were rarely detected or only were present in low concentrations in the effluent of the conventionally treated wastewater. vanA (9.14 × 10−1 cell equivalents/100 mL), and both mcr-1 and blaNDM belong to this category of rarely detected antibiotic resistance genes (Table 1).
Specific antibiotic resistance genes that have higher clinical relevance (like against vancomycin via the vanA gene and colistin via the mcr-1 gene) harbour a superior threat to human health than, for example, resistance against sulfamethoxazole (sul1). These critical ARGs are comparatively rare (Table 1, rarely detected), but can still be detected in the effluent after conventional treatment2,39. Due to their low concentrations, rarely detected, as well as some intermediately detected, ARGs are not suited for an evaluation of advanced treatment techniques, as they get frequently reduced below their detection limits without any evaluation of reduction efficiency. The ARGs with higher abundances are better suited for that purpose as, even after higher reduction efficiencies, the remaining cell equivalents can be detected5,40. Thus, for evaluation the frequently and intermediate occurring resistance genes blaTEM, tetM, sul1, CTX-M, CTX-M-32, blaOXA-48, and the class 1 integron gene intl1 were considered. As these ARGs, were originally also from anthropogenic fields, and are spread in the sewage system, they allow to predict the fate of rarely occurring resistance genes becoming distributed to the environment if no actions are taken to contain their spread41.
The investigated advanced technologies were two ultrafiltration membrane facilities and one ozone facility, which were run in parallel at the WWTP to assure analyses of the same inflow wastewater of the mentioned facilities (Fig. 1).
All advanced processes showed a strong reduction of facultative pathogenic bacteria compared to the cell equivalent abundances after conventional treatment. E. coli, A. baumannii, and enterococci were reduced below the detection limit by both ultrafiltration units (UF1 and UF2). The detection of the 16S rRNA gene marker representing Eubacteria was detected in higher abundances and was quantified with 1.35 × 103 for UF1 or 2.19 × 104 cell equivalents/100 mL for UF2 in the outflow water samples. This observation leads to the conclusion that ultrafiltration was not able to remove the entire bacterial community from the wastewater stream. Small bacteria or spores that pass the membrane, or flawed membrane installation, may allow bacteria to bypass the actual membrane and can be considered as a possible eubacterial contamination source42.
Ozone treatment with 1 g ozone/g DOC strongly reduced only A. baumannii with 3 orders of magnitude, while E. coli and enterococci got reduced with 2 orders of magnitudes at maximum. This reduction efficiency was less sufficient in comparison to the cell equivalents/100 mL found after ultrafiltration, with reductions up to 5 orders of magnitude. This also included the eubacterial 16S rRNA gene targets.
Ozone treatment using low concentration being optimized for micro-pollutant removal achieved a reduction of about 2 log units for the frequently occurring ARGs, resulting in concentrations varying from 2.18 × 102 (tetM) to 3.92 × 104 (sul1) cell equivalents/100 mL in the ozone facility outflow (Fig. 3). Both UFs strongly reduced these ARG targets to concentrations of less than 100 cell equivalents/100 mL (i.e. up to 6–7 log unit reductions). UF2 was not capable to remove the gene sul1 and the intl1 gene target below the detection limit, unlike the UF1 treatment. A number of 570 and 430 cell equivalents, respectively, of these frequently occurring genes were still present in 100 mL UF2 outflow, but still a 5 log unit reduction was found.
Considering the intermediately occurring ARGs (Table 1), ozonation resulted in a 4 log unit reduction of the β-lactamase genes CTX-M (against cephalosporins) and blaOXA-48 (against carbapenems). Bacteria carrying the resistance gene CTX-M-32 (β-lactamase against cephalosporins) were able to pass the ozonation facility to a greater extent, and was found in concentrations of up to 2.77 × 103 cell equivalents/100 mL in the outflow of the ozone facility. It has previously been reported that P. aeruginosa and GC-rich bacteria are capable of coping with the bactericidal effects of ozone and, as a consequence, can be present in the outflow of ozone facilities Therefore GC-rich bacteria carrying ARG like the CTX-M-32 gene might be able to pass the ozonation stage, demonstrating one mechanism of how ARGs can bypass this oxidative treatment method. These resistances can further be transferred to a wider variety of bacteria. But, UF1 and UF2 managed to reduce all intermediate occurring ARGs below their detection limits, thus supposing eliminating them from the conventionally treated wastewater (Fig. 3).
In addition, the level of significances varied between conventional treatment and ultrafiltration or ozonation. As E. coli and enterococci results generated p-values of 0.1 and 0.05 for ozone treatment, the treatment with UF membrane technology yielded in p-values of 0.01 for both E. coli and enterococci. The eubacterial 16S rRNA and A. baumannii reduction demonstrated a significance level of 0.05, which was independent of the applied treatment techniques (Fig. 2). Hence, ultrafiltration possessed stronger and more constant bacterial removal efficiencies. Ultrafiltration reduced facultative pathogenic bacteria and ARGs until a certain concentration threshold in the effluent was reached, whilst ozonation reduced contaminants only for a specific amount. More specifically, ultrafiltration was capable of reducing facultative pathogenic bacteria, as well as ARGs, close to the detection limit, independent of their initial concentration.
More generally, under the given process parameters, both advanced treatment technologies (ozonation and ultrafiltration) were able to reduce facultative pathogenic bacteria, as well as bacteria carrying antibiotic resistance genes, significantly. The membrane technologies especially were able to reduce a number of gene targets below or close to the detection limits. It was statistically confirmed that UF showed a more consistent ability to reduce gene targets in this way compared to ozonation, resulting in the higher p-values. It has to be mentioned that the applied ozone facility at the WWTP was adjusted to parameters be relevant for micro-pollutant removal13. Optimization of the ozone facility parameters like ozone concentration or hydraulic retention times for a more effective removal of both micropollutant but also microbial contaminations have to be discussed in future research approaches. Optimization efforts have recently been performed by Iakovides et al. utilizing rather low ozone concentrations between 0.125 and 0.75 g ozone/g DOC43. These authors showed that already low dosages and short hydraulic retention times are sufficient to eliminate parent compounds of e.g. antibiotics, but higher concentrations were needed to secure a sufficient and lasting reduction of bacteria and resistance genes. In general, higher ozone concentration inherits a rising risk of the formation of unwanted by products. Therefore special interest of a joint optimization process development needs to focus on prevention of formation and release of unwanted or harmful substances to the environment44,45. Unfortunately, this transformation processes can result in harmful by-products, which by themselves can have eco-toxicological effects up to a degree were the used ozonation as standalone process is questionable46. But, additional adsorption steps after ozonation would also be helpful to remove remaining ozone molecules and unwanted by-products, especially at higher ozone concentrations, which are supposed to harm the structural integrity of membranes in subsequent processes. Nevertheless, previous studies using additional filtration steps with charcoal or sand filtration downstream the ozonation inherit the risk of bacterial regrowth13.
For two additional sampling campaigns, the flux rates of both UF units were changed from 70 L/m²h to 12.5, 50, and 90 L/m²h for UF1, as well as 12.5 and 50 L/m²h for UF2. With only two independent samples, a deeper statistical analysis of this parameter variation was not feasible. On one hand, the UF1 membrane facility showed increased reduction efficiencies at higher flux rates. UF2, on the other hand, lacks the increased reduction effect with rising flux rates (see. SI Table 3). As both membranes showed different behaviours with an increasing flux rate, the membrane parameters seem to possess a stronger impact on the purification effects than the applied flux rates. For economic reasons, an increased flux rate could be advantageous depending on the increased energy consumption, as higher volumes could be processed by one filtration unit. Studies of ultrafiltration units used for drinking water treatment also propose the adjustment of operating parameters to maintain a constant transmembrane pressure at 1 bar or below, as it helps to reduce irreversible fouling47.
Cultivation of facultative pathogenic bacteria
Cultivation-based experiments were performed to demonstrate the presence of cultivable facultative pathogenic bacteria and bacteria resistant against ESBL antibiotics. Figure 4 shows the Colony Forming Units (CFU) calculated for 100 mL water sample volumes. Plate counts of the conventional treatment ranged from 8.70 × 103 CFUs/ 100 mL for enterococci, 1.70 × 104 CFUs/ 100 mL for Acinetobacter spp., and 8.19 × 104 CFUs/ 100 mL for E. coli.
Ozone treatment reduced cultivable E. coli, Acinetobacter spp., and enterococci by about 3 log units independent of their initial concentration after biological treatment. UF1 reduced facultative pathogenic bacteria below 1 CFU/100 mL water. Nevertheless, it was still possible to detect 3–10 CFUs in larger sample volumes of 1250 mL (data not shown).
Cultivated clinically relevant antibiotic resistant bacteria displayed in Fig. 4 show that resistant bacteria were present in the outflow of the conventional treatment with 1.74 × 104 CFU/100 mL of ESBL bacteria. All advanced technologies were able to strongly reduce the CFU numbers. Still some ESBL bacteria were also detected in the filtrate of UF1 and UF2, as well as after ozonation (28 CFUs after ozonation, 8 CFU after UF1, and 115 CFU per 100 mL after UF2).
The comparable reduction effect of ozonation and ultrafiltration in cultivation experiments might be impacted by the known limitations of cultivation methods. It is known that ozone induces a viable but nonculturable (VBNC) state rather than disrupt the bacterial membrane leading to cell lysis48. Such VBNC states can’t be detected through cultivation-based methods. Therefore, ozonation might yield higher reductions using cultivation methods rather than with molecular methods. Such molecular methods based on the same samples detected 113 E. coli cell equivalents/ 100 mL and 81 cell equivalents/ 100 mL of enterococci, whilst cultivation based methods only detected 48 CFU of E. coli and 4 CFUs of enterococci/ 100 mL. This leads to the assumption that the clinically relevant ESBL were also partly present in their VBNC states, and would regain their activity after longer incubation periods. This discrepancy could potentially lead to a higher human health risk if not taken into account.
Analysis of retentate
The presence of living bacteria in the retentate of membrane filtration is a major drawback of ultrafiltration technology. This is contrary to oxidative technologies like ozonation, where high fractions of bacteria become inactivated13. Bacteria, including facultative pathogenic bacteria and antibiotic resistant contaminants, are retained during ultrafiltration and get removed from the membrane during back-flushing steps. Thus, two sampling campaigns were performed where the inflow, as well as the retentate after a full filtration cycle (60 min), was analysed to control this situation.
It was demonstrated by the qPCR quantification of gene targets that the retentate water of UF1 harbours 2 log unit higher concentrations of facultative pathogenic bacteria compared to the inflow water. The 16S rRNA eubacterial gene marker increased from 3.46 × 106 cell equivalents in the UF inflow to 2.53 × 108 cell equivalents/ 100 mL in the retentate of UF1, indicating the general concentration of the bacteria. In contrast to the other facultative pathogenic bacteria, A. baumannii increased by only one order of magnitude in both UF units from 3.09 × 101 to 3.03 × 102 cell equivalents/100 mL. The abundance of ARGs under investigation in UF1 also demonstrated increased concentration values in ranges of 2 log units within the retentates. The gene blaTEM increased from 3.09 × 103 to 1.20 × 105 cell equivalents/100 mL, tetM accumulated from 5.34 × 102 to 2.76 × 104 cell equivalents/100 mL, and blaOXA-48 from 6.56 × 101 to 2.95 × 103 cell equivalents/100 mL. For cultivation experiments the above mentioned media systems and dilution steps were used to demonstrate cultivable facultative pathogenic bacteria in the retentates. Despite dilution at three different concentrations of the retentate the agar plates were mostly overgrown and not qualified for quantitative analysis. Nevertheless, living E. coli, enterococci. and Acinetobacter spp. were highly abundant in retentates.
In contrast to UF1, the concentration of facultative pathogenic bacteria, as well as most ARGs, in the retentate of UF2 were found in a lower degree of accumulation. Abundances of E. coli increased from 1.58 × 104 cell equivalents in 100 mL of the influent to 1.39 × 105 cell equivalents in 100 mL retentate. This observation hints at the suggestion that the membrane efficiency of UF 2 harbours an inferior retention capacity in comparison to UF 1.
A full list of the concentrations for each of the facultative pathogenic bacteria and ARGs in the retentate is listed in SI Table 4.
In addition to qPCR studies, metagenomic sequencing was performed to gain a more comprehensive overview about the genetic pool (resistome, virulence factors, and metabolic genes) to predict a possible risk of operation with the retentate. It is important to generate a deeper understanding of the overall antibiotic resistance and virulence gene levels of the retentate waters for their safe subsequent handling at the WWTP. It is calculated by the local WWTP engineers that retentate volumes of about 5,000 m3/day are expected after ultrafiltration of the daily waste waters. Therefore, decisions must be made about a possible recycling of the retentate back to activated sludge tanks, or inactivation of the retentate microbes by other means.
About 1,205 reads (UF1) and 1,201 reads (UF2) of retentate sequencing were successfully mapped against an antibiotic resistance gene data bank (Mvir DB). Herein, a cluster of ß-lactamases was found to contribute the majority (685 identified genes), followed by different tetracycline resistance genes (178 genes). Importantly, genes against the reserve antibiotics vancomycin (135 genes) and metallo-β-lactamase, i.e. with KPC carbapenemases and blaNDM genes (128 genes), were identified. Both KPC and blaNDM genes were handled separated from the remaining β-lactamases, as both provide resistances to nearly all known β-lactam antibiotic drugs49. Methicillin, erythromycin, and imipenem resistance genes were also detected, but in lower frequencies. Figure 5 displays the relative occurrence of the mapped antibiotic resistances. Due to the same inflow of both UF systems, the composition of the retentate resistome composition did not differ in any extent. The ß-lactamases contributed 56% of the overall resistome. Resistance genes against the last resort antibiotic vancomycin made up about 11% of the resistance genes, and was not expected to be so frequently identified. At least 31 vancomycin resistance genes of this operon were identified, including the vanA gene. Resistances against the veterinary and human-relevant tetracycline antibiotic comprised about 14% of sequences, the resistance genes against the less commonly used erythromycin is documented with 1%, and methicillin resistance genes were identified in less than 1% of reads. The rarely found methicillin resistances were identified via the resistance genes mecA and mecR1. Although imipenem is used quite rarely, a total of 13 different blaVIM resistance genes could be detected in the retentates. A list of identified resistance genes is shown in SI Table 5. The low relative abundances of erythromycin resistance genes in the metagenome of the retentate derive from the high variety of gene variants of other ARGs. For example, vancomycin resistance is mediated by 36 different genes, which were detected via metagenomic analysis, therefore despite vanA being categorized as a rarely detected resistance gene, vancomycin resistance take up 11% of the resistome. Erythromycin resistance was also found in the sample, but is only mediated by 7 different genes (SI Table 5). Thus, the frequently detected ermB genes, together with 6 other gene variants, take up a significantly lower proportion of the resistome.
According to the Mvir database mapping, the retentates of both UFs revealed a total of 792 (UF1) and 750 (UF2) pathogenicity islands as well as 120 (UF1) and 306 (UF2) different genes coding for virulence proteins. Amongst the 25 most identified virulence factors in both retentates were various transposases of the facultative pathogenic bacteria E. coli, K. aerogenes, P. aeruginosa, and Shigella flexneri as well as the Pseudomonas spp.-associated multiresistant ß-lactam transposon Tn1412. Additionally, 74 genes coding for protein toxins were found in the retentate of UF1 and 136 genes coding for protein toxins in the UF2 retentate.
Functional gene profiling revealed that, besides carbohydrate metabolism, a wide variety of genes involved in metabolic and biotransformation activities remained present in the retentate. The metabolic activity genes (6.38% for UF1 and 5.78% for UF2) and repair mechanisms genes (4.29% for UF1 and 4.35% for UF2) give hints towards the population activity and their capabilities of handling with stress responsive actions, such as their response to antibiotics or oxidative stress responses. A variety of at least 19 recombinase and integrase associated genes as well as 417 transposases associated genes amongst the functional genes further support the presumption, that the retentate can actively participate on horizontal gene transfer. Table 2 shows the most abundant functional gene categories.
Bacteria inherent to treatment plants, like Nitrosomonas spp. and Accumulibacter spp., that are involved in nitrogen and phosphorous biotransformation during biological treatment at WWTPs, were also identified in 0.2% and 0.3% of the taxonomic directed reads of the metagenome analyses, respectively. Therefore, the recycling of the retentates to the activated sludge tanks could support the growth of these slow growing beneficial bacteria, on the one hand. On the other hand, facultative pathogenic bacteria were present in similar concentrations and their higher growth rates could support a risk of accumulation of unwanted bacteria. They made up together 0.8% of the complete bacterial population, with E. coli comprising 0.4%, A. baumannii 0.3%, and enterococci 0.1%, respectively. Other clinically relevant bacteria were also detected with 0.4% of reads mapping to P. aeruginosa and 0.01% of reads mapping to Staphylococcus aureus. An overview of the composition of the species levels that made up more than 1% of the complete population is listed in SI Fig. 1.
Recycling of these facultative pathogenic bacteria might risk further accumulation, or even proliferation, within the biological treatment tanks. In this case an inactivation stage may be advantageous. It could be shown that the retentate harbours an elevated risk of promoting horizontal gene transfer potential through the high abundances of transposases within the bacterial community. As a consequence, recycling of these retentates back to activated sludge tanks might support horizontal gene transfer and the evolution of antibiotic resistances in bacterial populations. Therefore, a deeper understanding of the behaviour of these different kinds of bacteria after recycling is absolutely necessary for future technical operations at WWTPs.
The present study is demonstrating that technical measurements are already available to effectively reduce or eliminate antibiotic resistant genes and facultative pathogenic bacteria from municipal wastewaters at treatment plants. Both ultrafiltration and ozonation technologies demonstrated different removal efficiencies, but also distinct benefits and disadvantages. Ultrafiltration, as a physical technology, removed an average of 5 log units of both facultative pathogenic bacteria and ARGs, while ozonation adjusted to micro-pollutant treatment removed about 2 log units on average. In contrast to ultrafiltration, ozonation is known to effectively reduce micro-pollutants like antibiotic drugs or biocides by oxidative transformation, which might be helpful in reducing selective pressure on bacteria. Hence, future studies should include combined technologies like ozonation, with subsequent adsorptive filtration (charcoal or sand filtration), and membrane-based ultrafiltration to prevent environmental contamination, especially with antibiotic resistant, clinically relevant bacteria26. Such a proposed combination of oxidative, adsorptive, and membrane-based technology is illustrated in Fig. 6. Recently, it was calculated that about 2.66 × 1013 cell equivalents per day (i.e. antibiotic resistance genes and facultative pathogenic bacteria) reached the receiving body after conventional treatment. This discharge was significantly reduced to 6.5 × 108 cell equivalents per day of facultative pathogenic bacteria, including antibiotic resistance genes, when an ultrafiltration is performed. Finally, both technologies are valuable steps to interrupt dissemination of antibiotic resistant bacteria to the environment, as recommended by the WHO and UN assembly. It has to be pointed out that the present data of abundances and reduction efficiencies were obtained from only one specific treatment plant with its particular catchment area. It is difficult to introduce general kind of threshold values for wastewater conditioning processes, e.g. due to individual microbial growth dynamics and gene exchange capacities in receiving waters. Nevertheless, it could be demonstrated that both technologies, ozonation as well as ultrafiltration, were able reduce especially the most clinically relevant, but almost rarely detected ARGs (e.g. mcr-1, blaNDM-1, vanA, and blaVIM) and facultative pathogenic bacteria below the detection limit. In case of higher abundances combinatory efforts are recommended to reduce the antibiotic resistance determinants in a sufficient degree. In regard to technical and economic feasibility, an overall reduction of 4–5 log units (min. 99,99%) including ARGs and facultative pathogenic bacteria in higher abundances through the complete treatment plant could be a reasonable reference value.
Metagenomic raw data can be found at the NCBI database with the BioProject Accession number PRJNA524456. The data underlying Figs 2 and 3 are listed in SI Tables 6–9 and concrete p-values indicated in Figs 2 and 3 are displayed in the SI Table 10. The authors declare that the data supporting the findings of this study are available within the paper and its supplementary information files.
Feuerpfeil, I., López-Pila, J., Schmidt, R., Schneider, E. & Szewzyk, R. Antibiotikaresistente Bakterien und Antibiotika in der Umwelt. Bundesgesundheitsblatt - Gesundheitsforschung - Gesundheitsschutz 42, 37–50 (1999).
Hembach, N. et al. Occurrence of the mcr-1 Colistin Resistance Gene and other Clinically Relevant Antibiotic Resistance Genes in Microbial Populations at Different Municipal Wastewater Treatment Plants in Germany. Front Microbiol 8, 1282 (2017).
Jäger, T. et al. Reduction of Antibiotic Resistant Bacteria During Conventional and Advanced Wastewater Treatment, and the Disseminated Loads Released to the Environment. Frontiers in Microbiology 9 (2018).
Volkmann, H., Schwartz, T., Bischoff, P., Kirchen, S. & Obst, U. Detection of clinically relevant antibiotic-resistance genes in municipal wastewater using real-time PCR (TaqMan). Journal of Microbiological Methods 56, 277–286 (2004).
Czekalski, N., Berthold, T., Caucci, S., Egli, A. & Buergmann, H. Increased Levels of Multiresistant Bacteria and Resistance Genes after Wastewater Treatment and Their Dissemination into Lake Geneva, Switzerland. Frontiers in Microbiology 3 (2012).
Davison, J. Genetic Exchange between Bacteria in the Environment. Plasmid 42, 73–91 (1999).
Davies, J., Spiegelman, G. B. & Yim, G. The world of subinhibitory antibiotic concentrations. Curr Opin Microbiol 9, 445–453 (2006).
Schlüter, A., Krause, L., Szczepanowski, R., Goesmann, A. & Pühler, A. Genetic diversity and composition of a plasmid metagenome from a wastewater treatment plant. Journal of Biotechnology 136, 65–76 (2008).
Szczepanowski, R. et al. Insight into the plasmid metagenome of wastewater treatment plant bacteria showing reduced susceptibility to antimicrobial drugs analysed by the 454-pyrosequencing technology. Journal of Biotechnology 136, 54–64 (2008).
Jutkina, J., Marathe, N. P., Flach, C. F. & Larsson, D. G. J. Antibiotics and common antibacterial biocides stimulate horizontal transfer of resistance at low concentrations. Science of The Total Environment 616-617, 172–178 (2018).
Berendonk, T. U. et al. Tackling antibiotic resistance: the environmental framework. Nature Reviews Microbiology 13, 310 (2015).
Alexander, J., Bollmann, A., Seitz, W. & Schwartz, T. Microbiological characterization of aquatic microbiomes targeting taxonomical marker genes and antibiotic resistance genes of opportunistic bacteria. Science of The Total Environment 512-513, 316–325 (2015).
Alexander, J., Knopp, G., Dötsch, A., Wieland, A. & Schwartz, T. Ozone treatment of conditioned wastewater selects antibiotic resistance genes, opportunistic bacteria, and induce strong population shifts. Science of The Total Environment 559, 103–112 (2016).
Levy, S. B. & Marshall, B. Antibacterial resistance worldwide: causes, challenges and responses. Nature Medicine 10, S122 (2004).
Ternes, T. A. et al. Ozonation: a tool for removal of pharmaceuticals, contrast media and musk fragrances from wastewater? Water Research 37, 1976–1982 (2003).
Esplugas, S., Bila, D. M., Krause, L. G. T. & Dezotti, M. Ozonation and advanced oxidation technologies to remove endocrine disrupting chemicals (EDCs) and pharmaceuticals and personal care products (PPCPs) in water effluents. Journal of Hazardous Materials 149, 631–642 (2007).
Lüddeke, F. et al. Removal of total and antibiotic resistant bacteria in advanced wastewater treatment by ozonation in combination with different filtering techniques. Water Research 69, 243–251 (2015).
Somensi, C. A., Simionatto, E. L., Bertoli, S. L., Wisniewski, A. & Radetski, C. M. Use of ozone in a pilot-scale plant for textile wastewater pre-treatment: Physico-chemical efficiency, degradation by-products identification and environmental toxicity of treated wastewater. Journal of Hazardous Materials 175, 235–240 (2010).
Hunt, N. K. & Mariñas, B. J. Kinetics of Escherichia coli inactivation with ozone. Water Research 31, 1355–1362 (1997).
De Mora, S., Demers, S. & Vernet, M. The Effects of UV Radiation in the Marine Environment. (Cambridge University Press 2000).
Breazeal, M. V., Novak, J. T., Vikesland, P. J. & Pruden, A. Effect of wastewater colloids on membrane removal of antibiotic resistance genes. Water Res 47, 130–140 (2013).
Miehe, U. et al. “Abschlussbericht Projekt Akronym: OXERAM 2”, (2013).
Ek, M., Baresel, C., Magnér, J., Bergström, R. & Harding, M. Activated carbon for the removal of pharmaceutical residues from treated wastewater. Water Science and Technology 69, 2372–2380 (2014).
Dehouli, H., Chedeville, O., Cagnon, B., Caqueret, V. & Porte, C. Influences of pH, temperature and activated carbon properties on the interaction ozone/activated carbon for a wastewater treatment process. Desalination 254, 12–16 (2010).
Bai, R. & Leow, H. F. Microfiltration of activated sludge wastewater—the effect of system operation parameters. Separation and Purification Technology 29, 189–198 (2002).
Jäger, T. et al. Live-dead discrimination analysis, qPCR assessment for opportunistic pathogens, and population analysis at ozone wastewater treatment plants. Environmental Pollution 232, 571–579 (2018).
Clifford, R. J. et al. Detection of Bacterial 16S rRNA and Identification of Four Clinically Important Bacteria by Real-Time PCR. PLOS ONE 7, e48558 (2012).
Rocha, J. et al. Inter-laboratory calibration of quantitative analyses of antibiotic resistance genes. Journal of Environmental Chemical Engineering (2018).
Peak, N. et al. Abundance of six tetracycline resistance genes in wastewater lagoons at cattle feedlots with different antibiotic use strategies. Environmental Microbiology 9, 143–151 (2007).
Paterson, D. L. et al. Extended-Spectrum β-Lactamases in Klebsiella pneumoniae Bloodstream Isolates from Seven Countries: Dominance and Widespread Prevalence of SHV- and CTX-M-Type β-Lactamases. Antimicrobial Agents and Chemotherapy 47, 3554–3560 (2003).
Monteiro, J., Widen, R. H., Pignatari, A. C. C., Kubasek, C. & Silbert, S. Rapid detection of carbapenemase genes by multiplex real-time PCR. Journal of Antimicrobial Chemotherapy 67, 906–909 (2012).
Volkmann, H., Schwartz, T., Kirchen, S., Stofer, C. & Obst, U. Evaluation of inhibition and cross-reaction effects on real-time PCR applied to the total DNA of wastewater samples for the quantification of bacterial antibiotic resistance genes and taxon-specific targets. Molecular and Cellular Probes 21, 125–133 (2007).
Kurpiel, P. M. & Hanson, N. D. Point mutations in the inc antisense RNA gene are associated with increased plasmid copy number, expression of blaCMY-2 and resistance to piperacillin/tazobactam in Escherichia coli. Journal of Antimicrobial Chemotherapy 67, 339–345 (2011).
Klein, G., Pack, A. & Reuter, G. Antibiotic Resistance Patterns of Enterococci and Occurrence of Vancomycin-Resistant Enterococci in Raw Minced Beef and Pork in Germany. Applied and Environmental Microbiology 64, 1825–1830 (1998).
Zhou, C. E. et al. MvirDB–a microbial database of protein toxins, virulence factors and antibiotic resistance genes for bio-defence applications. Nucleic acids research 35, D391–D394 (2007).
Langmead, B., Trapnell, C., Pop, M. & Salzberg, S. L. Ultrafast and memory-efficient alignment of short DNA sequences to the human genome. Genome Biology 10, R25 (2009).
Li, J. et al. An integrated catalog of reference genes in the human gut microbiome. Nature Biotechnology 32, 834 (2014).
Wood, D. E. & Salzberg, S. L. Kraken: ultrafast metagenomic sequence classification using exact alignments. Genome Biology 15, R46 (2014).
Obst, U., Schwartz, T., Jansen, B. & Kohnen, W. Detection of antibiotic-resistant bacteria and their resistance genes in wastewater, surface water, and drinking water biofilms. FEMS Microbiology Ecology 43, 325–335 (2003).
Czekalski, N., Gascón Díez, E. & Bürgmann, H. Wastewater as a point source of antibiotic-resistance genes in the sediment of a freshwater lake. The Isme Journal 8, 1381 (2014).
Zhang, X.-X., Zhang, T. & Fang, H. H. P. Antibiotic resistance genes in water environment. Applied Microbiology and Biotechnology 82, 397–414 (2009).
Ottoson, J., Hansen, A., Björlenius, B., Norder, H. & Stenström, T. A. Removal of viruses, parasitic protozoa and microbial indicators in conventional and membrane processes in a wastewater pilot plant. Water Research 40, 1449–1457 (2006).
Iakovides, I. C. et al. Continuous ozonation of urban wastewater: Removal of antibiotics, antibiotic-resistant Escherichia coli and antibiotic resistance genes and phytotoxicity. Water Research 159, 333–347 (2019).
Weschler, C. J. New Directions: Ozone-initiated reaction products indoors may be more harmful than ozone itself. Atmospheric Environment 38, 5715–5716 (2004).
Weschler, C. J. Ozone’s impact on public health: contributions from indoor exposures to ozone and products of ozone-initiated chemistry. Environ Health Perspect 114, 1489–1496 (2006).
Mulder, M., Antakyali, D. & Ante, S. Costs of removal of micropollutants from effluents of municipal wastewater treatment plants-general cost estimates for the Netherlands based on implemented full scale post treatments of effluents of wastewater treatment plants in Germany and Switzerland. STOWA and Waterboard the Dommel, The Netherlands 55 (2015).
Crozes, G. F., Jacangelo, J. G., Anselme, C. & Laîné, J. M. Impact of ultrafiltration operating conditions on membrane irreversible fouling. Journal of Membrane Science 124, 63–76 (1997).
Zhang, Y. Q., Wu, Q. P., Zhang, J. M. & Yang, X. H. Effects of ozone on membrane permeability and ultrastructure in Pseudomonas aeruginosa. Journal of Applied Microbiology 111, 1006–1015 (2011).
Pesesky, M. W. et al. KPC and NDM-1 genes in related Enterobacteriaceae strains and plasmids from Pakistan and the United States. Emerging infectious diseases 21, 1034–1037 (2015).
We thank the BMBF for financial support within the framework of the HyReKA-project (02WRS1377BB) as part of the RiSKWa-program. The HyReKA research project is also headed by Prof. Dr. Martin Exner (University Clinics Bonn, Germany. We acknowledge support by Deutsche Forschungsgemeinschaft and Open Access Publishing Fund of Karlsruhe Institute of Technology. We also thank Dr. Chistophe Merlin (University of Lorraine, Nancy) providing the E. coli reference strain carrying the pNORM plasmid.
The authors declare no competing interests.
Publisher’s note: Springer Nature remains neutral with regard to jurisdictional claims in published maps and institutional affiliations.
About this article
Cite this article
Hembach, N., Alexander, J., Hiller, C. et al. Dissemination prevention of antibiotic resistant and facultative pathogenic bacteria by ultrafiltration and ozone treatment at an urban wastewater treatment plant. Sci Rep 9, 12843 (2019). https://doi.org/10.1038/s41598-019-49263-1
Evaluation of antibiotic resistance dissemination by wastewater treatment plant effluents with different catchment areas in Germany
Scientific Reports (2020)
An alternative material for an effective treatment technique proposal in the light of bibliometric profile of global scientific research on antibiotic resistance and Escherichia coli
Environmental Monitoring and Assessment (2020)